First, the use of features
1. Long-term allowable operating temperature of cable conductor: Polyvinyl fluoride, polyethylene insulation should not exceed 70 ° C; XLPE insulation should not exceed 90 ° C.
2. The laying temperature of the cable should not be lower than -20 °C
3. Allowable bending radius of the cable: the outer diameter of the cable (D) is less than 25mm and should not be less than 4D; if the outer diameter of the cable (D) is 25MM or more, it should be no less than 6D.